How to repair Gauge
Sometimes your Gauge needle is back and forth from 0 PSI then how we can repair and adjust Needle at 0 PSI we can easily repair this fault.
we should open his Blue or Red Cover and after this open his Plastic glass rotate the plastic glass anti clockwise So its plastic Glass will open.
when his Plastic Glass will open then you can see a screw you adjust needle by rotate screw clockwise or anti clockwise .
When the needle is set to 0 PSI then you should close his Glass and Cover. Now e your Gauge will work perfectly.
If you don’t understand you can watch video down.
Watch Video how repair Gauge
You should read it :
- How to reduce electricity bill at home,Best 3 ways
- How to change Rusty bearing of any Motor
- Best way gas store AC (air conditioner) with connect manifold gauge
- Q and A RAC / HVAC |Compressor, Capacitor, Suction Ice, Overload AC ?