In English Ammonia Gas Uses and Effects Ammonia Gas Uses and Effects : This Gas Use in Cold Storage Plant. Ammonia Gas formula is NH3. Ammonia Gas Boiling Point is -33.34 °C Ammonia Gas Freezing Point is -77.37 °C Liquid Condition of Ammonia Liquid Condition of Ammonia Gas is more Dangerous. If Ammonia Gas falls on
Refrigerant R600a Dangerous: Refrigerant R600a is a Dangerous Gas we should Charge this Gas very Carefully. This Gas is a Flammable Gas. If we put the gas fire so gas can be on fire and Cylinder will be Blast. If we charge this Gas we should not use Gas welding near this. Refrigerant R600a Use
How to transfer Gas from Outdoor to Cylinder If we have Gas in Outdoor unit and we want save Gas in Cylinder. we can do it easily. we need some tools for save Gas in cylinder. Tools we need : 3 Line 1 Gauge 1 refrigerator Compressor Empty Gas Cylinder Store gas in Outdoor and
How to Trace fault with Gas Pressure & Line Gauge We can Trace some fault with running and standing pressure. when AC is turn ON then the pressure that appears on the gauge is Running Pressure and when AC is turn OFF then the pressure that appears on the gauge is Standing Pressure. R22 Normal
FAQ’s R32 Why is R32 Required? The Main Pillars of the new EU F-Gas Rules are to reduce emissions and to move towards lower GWP solutions. This involves a phase down in the consumption of HFCs and a reduction of 37% by 2020 and 79% by 2030. By 2025 Single Split A/C systems with less
Gas Pressure high Sometimes our AC gas pressure is high It does not mean we should remove the gas. if our piping is long 40-50 ft we can charge more gas. If our AC is in the sunlight Still the pressure will look more. we should charge Gas with weight. Some AC ready on 75
Window AC ICE on Pipe If ice coming on your Windows AC Piping. Turn your AC on and You should check your running gas pressure with line Gauge. R22 refrigerant Running back pressure is 65 PSI. If your Gas is low you should charge your Gas and if your Gas is high you should reduce your
Split AC Outdoor Gas Valves Sometimes the gas valves are leaked. When gas valves are damaged. They are gas valves. From where we close the gas and open with L key. When gas valves are damaged. We Should change Gas valves. Sometimes We checked all the gas leak point but We not check gas valves.
GAS low problem in AC If your AC’s drain Blocked So the water falling into the room. In this Condition we should do Service AC. But I did check the AC that Ac’s drain is Clear and AC are already serviced. But the water falling into the room. Then i check Gas that Gas is
Vacuum is necessary before charge gas in Air Conditioner.