How trac high, medium,low speed wire indoor fan motor
How trac high, medium, low speed wire indoor fan motor
How to find Common, Running, Starting and High, Medium, Low wire in indoor fan Motor
First of all we should find Starting and Running Wire and then we can find High, Medium, Low wire easily.
We should set Meter Point at continuity for Check Resistance Reading
After Set meter continuity we do start find reading one by one, In the two wires Will get more readings, They will be Starting and running.
when We will find Starting and Running wire So how will we know which wire is running and which wire is Starting.
when We will find Starting and Running wire The rest of the wires will be Common, Those who will be high, medium, and low , All high, medium, and low Wires is Common wires, Only difference is in their speed
One wire of meter put any Common high, medium, and low wire and second wire of meter put running or starting and get reading, which wire will show more reading with common wire between running and starting, this wire will be starting wire.
Now we can find easily High, Medium, Low wire. one wire of meter put starting wire and second put one by one all Common wires and you can see reading on meter Note reading, which wire will show more reading with with starting wire, this wire will be low speed wire and which wire show medium reading this will be Medium Speed wire and Which shows the lowest reading This wire will be High Speed wire.
Privacy & Cookies Policy
Necessary cookies are absolutely essential for the website to function properly. This category only includes cookies that ensures basic functionalities and security features of the website. These cookies do not store any personal information.
Any cookies that may not be particularly necessary for the website to function and is used specifically to collect user personal data via analytics, ads, other embedded contents are termed as non-necessary cookies. It is mandatory to procure user consent prior to running these cookies on your website.